The developer shall perform, as a minimum, the following tests and provide the district written documentation of the date performed and results obtained. Pump tests shall meet or exceed specified capacity. The district shall be informed of the testing schedule 48 hours prior to the test and shall be present during testing.
(1) Pump capacity by drawdown test.
(2) Control panel operation.
(3) Generator load test.
(4) Automatic transfer reconciled to auxiliary power and back to utility power.
(5) Telemetry control to terminal strip.
(6) Telemetry control to SCADA system.
(7) Pump vibration analysis.
Fill water for testing shall be obtained in accordance with district cross connection practices. [Res. 735 § 1, 2017.]